Tank Monitor - Positioning
- The tank monitor should be installed at least 300mm above the highest possible water level. 200mm is the minimum measurable distance above the highest water level.
- The sensor should be as close to level as possible, at no more than a three degree angle. Mounting shims are available if your tank has a curved top.
Ensure that there are no obstructions directly under your chosen mounting position such as ball cocks, inflow and outflow pipes.
The sensor should be as close to level as possible, at no more than a three degree angle. Make sure that the sensor position is at least 300mm above the highest water level. The maximum range of the sensor is 3.6m.
The best installation spot is on the center of the tank roof. This is usually the highest point and allows a clear view to the water surface.
If the center of the tank is not flat, there are alternative options:
The sensor can be installed on the tanks access lid. This is not the best position as false alarms can be triggered if you happen to remove the tank lid for inspection.
Mounting high (but off center) using the mounting shims is the standard method for installation on concrete tanks. Some customers prefer replacing the inspection lid with timber to attach the sensor.